I'd think that the fact that cold air is coming from the two right vents would eliminate the possibility that the problem is in the compressor-condenser-evaporator loop, unless there are two separate evaporators, for the right and left side. Sounds more like a controls and/or damper problem.So 110 degree temps this week is really pressing on the A/C system from morning till home after work.
Clarity's A/C is now blowing hot air on the left 2 vents and cold air on the right 2 vents.
Turned off Sync, switched to manual, low speed vs high speed, max A/C = no change.
Is the refrigerant low or the dampers not working?
Any A/C experts here ?
I am decidedly not an "A/C expert".